Dry-coolers since heat transfer is not accompanied by moisture exchange. The process takes place on the principle of heat exchange only transparent. The design of the liquid coolers is based on: water-air exchanger, fans (mostly axial, although there are also special designs with radial fans), automatic control system (whose function is to maintain the set water temperature), casing with legs. Constant efforts by manufacturers to achieve the highest possible performance and the smallest dimensions have resulted in a modification of traditional sprinkler solutions that increase the intensity of heat exchange by evaporating water. So we are currently dealing with ready-made products available on the market, called drycoolers with "water spray" function. The water spray system consists of spray nozzles, nozzle solenoid valves (two valves allow two-stage regulation of the amount of sprayed water), distribution lines with pressure gauge on the main manifold, manual emptying valve or automatic system Draining, activated when the system is to be shut down, low pressure switch indicating that the water supply pressure is too low. The operation of standard equipment (dry dry-coolers) involves the exchange of heat between water and atmospheric air. A heat exchanger shaped as a finned coil transfers heat to the outside air. Dry cooler category keywords:
dry cooler, dry air coolers, dry air cooler, dry cooler hvac, dry cooler price, dry fluid cooler, dry air cooler price, adiabatic dry cooler, adiabatic dry air coolers, carrier dry cooler, dry cooler for home, dry cooler operation, hybrid dry cooler, dry air cooler for home, liebert dry cooler, dry cooler manufacturers, dry cooler price list, dry cooler vs cooling tower, dry coolers inc, liebert dry coolers, trane dry cooler, dry cooler wiki, dry cooler definition, what is a dry cooler, alfa laval dry cooler, thermokey dry cooler, refrion dry coolers, fluid cooler vs dry cooler.